Please tell me you need master or slave panel after order. if you do not have a master panel, the salve panel is the best choice.
One Master Panel could connect 1 to 31 slave panels.
When the slave panel has alarm or fault event, the slave panel would send even to master panel, and then master would show the event of slaves one by one.
Mater panel connect all the slave panel with RS485 communication port, Each panel RS485 port have two terminals A and B, all the terminal A should be connected in one wire, and also terminal B should be connected in another wire.
Also the DC24V power of panels should be connected together.
One master panel can connect 5 slave panels with 2 amp power supply, if need connect more slave panels then must update power supply.
The information provided in this manual covers the Master and Slave fire alarm control panel. The panel range is designed to meet the requirements of EN54 Parts 2 & 4.
The fire alarm control panels 2 Zones) provide all of the sophisticated features required of a leading edge conventional fire alarm system along with the simple operation and efficient installation methods demanded by both installers and building users.
A comprehensive range of auxiliary devices is available to operate with the fire control panels including optical, ionization, photoelectric, photoelectric-thermal and heat detectors.
Each of the system components has been specifically designed to operate as part of the system. This provides assurance that the control panel, smoke detectors, interface devices and the ancillary components are all fully compatible with one another and that the full range of system functionality is supported by each device.
The panels have the following key features:
· 2 conventional input zones.
· 1 notification appliance circuits (NAC) with built-in synchronization for ANSI 3.41and Gentex.
· The panel comes with a 2 amp power supply.
· Dedicated alarm and trouble relays.
· 1 RS485 can be able to connect the other panel.
· Housed in a 205mm W x 258mm H x 81mm D metal enclosure.
· Enclosure supports two 12V, 4Ah backup batteries.
120VAC 50/60 Hz Power supply rating
240VAC 50/60 Hz
Power supply rating
2 Amps @ 24VDC
Maximum Battery Charging Current
0.98 Amps @ 26VDC
Initiating Device Circuits 2 Zones
Alarm Zone 2
Normal Initiating Operating Voltage
23VDC, Maximum 26VDC, regulated
Normal Quiescent Current (normal status)