Free shipping High quality Wall Mount Motion Sensor Automatic PIR Infrared Sensor Light Switch 9m Max (ET033)
Noted: This product only works in the dusk or evening when the ambient light is less than 20 LUX or no any light in the surrounding environment.
The product adopts good sensitivity detector, integrated circuit. It gathers automatism, convenient safe, saving-energy and practical functions. It utilizes the infrared energy from human as control-signal source, it can start the load at once when one enters detection field. It can identify day and night automatically. It is easy to install.
Remote Control Wall Switch
800W/110V (incandescent lamp)
PIR Motion Sensor Switch
1.It can only work in the ambient light less than 20LUX (dark).
2.Time-delay is added continually: When it receives the second induction signals after the first induction, it will compute time once more on the rest of the first time-delay basic (set time).
3.Time-delay adjustment: It can be set according to the consumer\'s desire. The minimum time is 10sec±3sec. The maximum is 7min±2min.
4.The switch: The switch is “ON”,“OFF”,“AUTO”.
1.Shut off the power.
2.Loosen the connection column on the bottom of sensor, plug the wire into connection hole, tighten the screws; unload the surface of sensor, connect the sensor into connection box.
3.Cross the installation screws into installation hole of sensor, aimed at the hole of 4.connection box, tighten the screws, cover the surface of sensor.
5.Switch on the power then test it.
CONNECT-WIRE FIGURE(See the right figure):
1.Set the function switch to “ON”, turn the TIME knob anti-clockwise on the minimum after taking the board-face off.
2.Switch on the power, the lamp should be on;
3.Set the function switch to “OFF”, the lamp should be off immediately, all functions should be in “stop” state.
4.Set the function switch to “AUTO”, after 30sec later, it enter into working position, the lamp will be turned on after receiving the inductor signal. Under no inductor signal condition, the lamp should be off within 5~10sec, the lamp should be on again after 5sec.
1.Electrician or experienced human can install it.
2.The unrest objects can\'t be regarded the installation basis-face.
3.There aren\'t hinder or unrest objects effecting detection in front of the detection window.
4.Avoid installing it near temperature alteration zones, for example: air condition, central heating etc.
5.Please don\'t open the case for your safety if you find the hitch after installation.
6.If there are some difference between instruction and the function the product has, please give priority to product and sorry not to inform you additionally.
Infrared Sensor Light Switch
SOME PROBLEM AND SOLVED WAY:
1.The load don\'t work:
a. Checks the power and the load.
b. If the load is good.
c. If the indicator lamp speeds quicken after induction. Please check if the switch is on the “auto” position if the speed quicken.
d. Please check if the working light corresponds to the ambient-light.
2.The sensitivity is poor:
a. Please check if in front of the detection window there is hinder that effect to receive the signals.
b. Please check the ambient temperature.
c. Please check if the signal source is in the detection field.
d. Please check the installation height.
e. If the moving orientation is correct.
3.The sensor can\'t shut off the load automatically:
a. If there is continual sensor signal in the detection field.
b. If the time-delay be set to the longest.
c. If the power correspond to the instruction.
d. If the temperature change near the sensor. Such as air condition, central heating etc