Regional LPZ 2-3 for lightning or higher interface area, generally used for a variety of low-voltage, single phase, fine third of DC electronic devices (D) overvoltage protection
TPS D10-12V TPS D10-24V TPS D10-48V TPS D10-60V TPS D10-120V TPS D10-230V
TPS D10 Series modular low-voltage power surge protector is a single module, rail-mounted terminal device level (tertiary classification test) surge absorption protection, suitable for single or multi-phase low voltage power supply options, easy installation, simple . Built-in protection circuit, the gas discharge tube and varistor structure, and is an overheating cut-off device monitoring. In the protection circuit suffered greatly over frequent power surges or overloaded, the cutting device will overheat protection circuit with the grid separation, so that the grid is not affected; Meanwhile, the red LED warning lights, prompting the user to protect the circuit has expired, protector installation lose its protective role in the downstream electronic equipment, the user must replace the protector immediately. Protection also has a green LED lights, indicating the power call. Disconnect contacts with remote signaling alarm device, as an additional optional feature, available on user requirements.
1 through flow, residual voltage, fast response, no freewheeling
2 Built-in thermal tripping device, so protection from overheating, breakdown failure can automatically disconnect
3 standard 35mm rail mounting modular design, very easy to install and maintain
4 There continue to detect the working status indicator, red LED when the circuit failure warning lights, green LED lights indicate working status
5 LN-PE full protection mode is more secure, small space
35mmElectrical installation guide to install a standard module width, 35mmDIN-rail, 1 modulo number
Fine surge protection devices can be used as the power section of the terminal equipment can be used for lightning regional LPZ2-3 or higher interfacial area, widely used in computers, modems, ripple control equipment, industrial control systems and measurement systems, protecting them from the lightning or over-voltage surge caused damage to the switching operation. Selected according to the specific choice of system voltage corresponding products, 12V, 24V, 48V, 60V, 120V, 230V voltage optional six. Comprehensive surge protection, you also need to install the Class B and Class C lightning over-voltage protection.
Usually installed in front of the equipment, the power phase line L, N, respectively, the zero line surge protector corresponding access terminals to ensure secure and reliable, because the built-in thermal cut-off device, no need to pre-empty open or fuses, while the electric surge protector ground and ground to make a good electrical connection.
Surge protectors should regularly check the work, the protection circuit suffered greatly over frequent power surges or overloaded, the cutting device will overheat protection circuit with the grid separation, so that the grid is not affected; while red LED warning lights, prompting the user to protect the circuit lapsed protection for electronic equipment installed in the downstream loses its protective effect, the user must be replaced immediately protector.